And since the un-named post didn't go to the elog (or email), here it is again.
Please read through to the end to see the discussion on the Emergency Power.
When the house power feed to the EM circuit that when the breaker was cycled we lost the primary feed to the
EM transfer swith and the alternate feed switched on through the Automatic Transfer Switch.
This resulted in a short (2-3 second) loss of power to items on the Emergency Loop.
All systems restored except for the computer and extractor gauge monitoring vacuum at/near the HV chamber.
Please note that the Emerg
First thing this morning restored power to Picoameters in the Injector Service building and powered on the GPIB interface module. GPIB device not establishing gpib comm so I had to do a soft reboot of IOCSOFTINJ1. IOCSOFTINJ1 is hung up. Clicking on check IOC from IOCSOFTINJ1's control screen and a screen pops up indicating
Processing...... IOCSOFTINJ1 No Such Map Netgroup. Reason: Can't communicate with port mapper
I don't know what that means so software will have to take a look at this.
Leonard Page & I came in Saturday to look at hoses that needed to be fixed and replaced. Friday Evonda & I did the cable measurements for the FWD & REF of the SSAs' 1-8. Sunday made & installed the new hoses for CMTF. I also found & measured 15ea 20db attenuators for the LERF amp power test.
I also found the LCW Flow problem !!!!!!!!!! let's just say I fixed it (he he).