Notes from T_Dela Cruz about the power supply used for the
Wien Filter Switcher chassis hi-potting:
-Using the Vacuum System's Hi-potronic DC power supply.
-Voltage was ramped up in 1kV increments and allowed it to
settle for 1 minute.
-Closely monitored the ampere meter on the front display for
current leakage starting at 15kV.
-Positive input channel was very stable up to 30kV, then it
-Negative input channel did not overload fault at 30kV.