Today we identified several valves that had the limits wired backwards; we fixed them and all the valves in the lower MeV region are reading correctly; Valves VBVM501, M601, and M701 have all been cycled and checked with interlock. Also, I had several UHV status indicators in the firmware with flipped polarity; those have been corrected as well.
Software is making some updated to fix a couple UHV indicators on the screen that are incorrect, and improve the functionality of the valve opening buttons. We will verify this tomorrow.
At the moment I'm unable to open the QCM valves.
The FCD is complete.
Both JT valves are set to stable conditions and controlling the LL at 90%.
Both CD valves have been locked at 0%.
All the heaters on CM05 are set to 5W.
All the heaters on CM16 are set to 5W.
The vault will remain in ODH2 until pump down in the morning.